来源：https://www.sdqyjn.com/ 日期：2021-05-26 浏览量：
In modern enterprises, the use of compressed air is more and more common. The common compressed air dryers are adsorption dryer and freezing dryer. What is the difference between freeze dryer and adsorption dryer?
1. Different working principles
冷干机是根据冷冻除 湿原理，将来自上游的饱和压缩空气通过与冷媒的热交换冷 却到一定的温度，凝析出大量的液态水，经气液分离器分离后自动排出机外，从而达到除水干燥的目的。吸干机则是根据变压吸附的原理，将来自上游的饱和压缩空气在一定的压力下经过与干燥剂的接触，将绝大部分的水份吸附在干燥剂里，干燥空气进入下游工作，从而达到深 度干燥的目的。
According to the principle of freezing dehumidification, the chiller cools the saturated compressed air from upstream to a certain temperature through heat exchange with refrigerant, condenses out a large amount of liquid water, and automatically discharges it out of the chiller after separation by gas-liquid separator, so as to achieve the purpose of water removal and drying. Suction dryer is based on the principle of pressure swing adsorption, will come from the upstream saturated compressed air under a certain pressure through contact with the desiccant, the vast majority of moisture adsorption in the desiccant, dry air into the downstream work, so as to achieve the purpose of deep drying.
2. Different water removal effect
冷干机因为受到其原理的制约，如果温度太低的话会出现结冰现象，所以其的温度通常在2~10℃。吸干机则因为无须通过温度变化，而干燥剂（氧化铝）则又可以进行深 度干燥，所以通常其出口的温度可以达到-20℃以下，也就是说可以达到深 度干燥。
Because of its principle, if the temperature is too low, there will be icing phenomenon, so its temperature is usually 2 ~ 10 ℃. The suction dryer does not need to change the temperature, and the desiccant (alumina) can carry out deep drying, so the outlet temperature of the suction dryer can reach below - 20 ℃, that is to say, it can achieve deep drying.
3. Difference in energy consumption
For the cold dryer, because the purpose of cooling can only be achieved through refrigerant compression, so the power supply will be high. As long as the valve is controlled by the electric control box, the power consumption of the suction dryer is usually only about tens of watts, that is to say, there will be no power loss.
4. Difference of gas loss
因为冷干机是通过变温来达到除水的目的，水份又是通过自动排水器排出机外，所以没有气量的损耗。而吸干机则因为干燥剂在吸水饱和后需要再 生，因些需要有12-15%左右的再 生气损耗。
Because the cold dryer is to achieve the purpose of water removal by changing the temperature, and the water is discharged from the machine through the automatic drainer, so there is no loss of air volume. The dryer needs to be regenerated after water absorption saturation, so it needs about 12-15% regeneration gas loss.
5 different failure rates
Because the refrigerant system and air system of the dryer, including the electrical part, are relatively complex, and only the valve of the dryer has the possibility of failure due to frequent action, so in general, the failure rate of the dryer is lower than that of the supercooled dryer.
Generally speaking, the suction dryer is better than the cold dryer in terms of stability and effect, just because it needs to consume a certain amount of regeneration gas, so we usually ask customers to weigh the pros and cons before making a choice. But now there are more and more manufacturers choose suction dryer, it should be said that this is gradually becoming a trend