Q Q: 506615608
The layout sequence of each equipment of nitrogen generator is connected according to the process flow. Users need to put forward the size drawing of equipment installation workshop and the location of air inlet and finished nitrogen outlet in advance, and plan the layout and connection diagram of the whole set of nitrogen generator equipment according to the actual site conditions.
Generally, there is no site foundation requirement for nitrogen generator system equipment, so long as the flat floor in the plant can meet the installation conditions. However, for larger specifications of air compressor, compressed air drying equipment, etc., it shall be implemented according to the requirements of the manufacturer. For the convenience of equipment maintenance and cleaning, it is best to make a flat table 10 cm above the ground in the air compressor, drying equipment, nitrogen generator and nitrogen purification device.
The equipment is generally arranged along the plant wall. The air compressor and cold dryer should be placed at the upper air outlet or in a well ventilated place. If there is no air storage tank behind the air compressor, the distance between the air compressor and the cold dryer should be as large as possible, and the pipeline length between the two should be as long as possible, so as to reduce the compressed air temperature through the atmospheric environment. The distance between each equipment shall be at least 1 m, and the distance between each equipment and the wall shall be at least greater than 0.8 M. the operation surface of the equipment shall be oriented to facilitate the operation, maintenance and repair of the equipment by the users.
The pipeline connection between the equipment depends on the actual situation after the equipment is in place. It is recommended that the pipeline connection be made by the user according to the needs. It is better to use hard connection (thread connection or welding) for all pipelines, and the construction should be carried out by professionals to avoid leakage.
3. Installation requirements of nitrogen generator
The user is responsible for the installation of the equipment and is responsible for guiding the installation of the equipment.
After all process equipment is in place, the pipeline between the equipment shall be configured according to the actual situation on site. All pipelines shall be hard connected (threaded connection or welding) and constructed by professionals to avoid leakage. It is the best to use copper or stainless steel pipe for the pipeline between the nitrogen outlet of finished product and the gas consumption point (the new galvanized pipe shall be used at the latest), and the connection shall be made by welding.
The power supply and cooling water shall be led to the equipment site, and the distribution board and cooling water supply facilities shall be prepared.